Sorry gents, fell asleep, long day. But, my trany went out last Sat of instead of getting it fixed they gave m a brandy new "2013", dang, it even got a back up camera in the rear view mirror!
Anyway, for the short time it runs 50 suct and 150 disch. I changed the dual cap with a 35/6 ( I don' even remember where I got this from ) there was a 35/5 in there. The contactor in pulled in the whole time. The fan runs strong for a minute and slowly just slows to a stop and the comp is still energized.
I have changed qutie a few cap, contacs, fan motors, etc, but I don't consider myself a "tech" in this particular field. O2N2, Aux Equip those are my "tech" areas and even refrigerators I do a lot beter.
I'm starting to think i have a problem with the reversing vlv or defrost cycle. For this unit to run for less than 2 minutes and have the amout of heat I can feel coming up from the unit I say hot disch gas or a heating cycle in interfering with the cooling cycle. I believe just because I hear it shift dosen't mean it "fully" shifted, that's my concern.
I would have given a wrench set if I won to the tech that gave me the best/most help but I entered a contest that was over a month ago. lol