The sealed system is not able to alleviate the superheat picked up during the refrigeration process. This could mean :
1. Low charge
3. Condenser motor not up to speed
4. Bad reed valves in compressor (inefficient compressor)
Just my first thoughts. Probably needs a tap valve installed to check out the pressures.