A free world-class appliance repair website for everyone.Connect with appliance repair technicians from the U.S. and Canada.Download free service manuals, wiring diagrams, tech sheets and more.
high Low165 40150 25150 23 (psi)Temperature external of evaporator 49.5F at 23 psi (shoud be -2F)Temperature external of condenser 97 F at the fan at 150 psi (shoud be -82.5F)Fitting at the condenser are full of ice and evaporator his starting to fill up too.Thank you
I bet it has something to do with how the pipes connect from the evaporator to the outside condenser. How did you make up the connections?
Please add a pic because this is all becoming perfectly clear now. Your tubing is too small. The minimum is 3/8ths tubing for the hi side and 5/8th for suction.